There are Ten Fiberglass Cooling Towers located on the roof of the powerhouse at this facility all with badly damaged fill media resulting in loss of thermal performance as well significant water splash out of the loose damaged fill sheet, resulting in ice building up and corrosion of the supporting steel structure.
The original PVC hung fill media sheets on nine of the cooling towers were removed and replaced with bottom supported Brentwood XF75 high efficiency fill media specifically designed for Cross Flow Cooling Towers, complete with integral inlet louvers and additional separate high efficiency drift eliminators, bottom supported to facilitate cleaning and maintenance. The separate drift eliminators were installed to further reduce drift loss.
CELESTICA Cross Flow Cooling Tower Repair
This project was completed on time and n budget during January 2012.